The U.S. Army Corps of Engineers Research Lab (USACE ERDC/CERL) has published data collected during a 24-month demonstration/validation project in which the Zeta Rod® Water Management System was evaluated for its ability to deliver documented water conservation results while providing corrosion, scaling, and biofouling protection in open-loop evaporative cooling systems. The report, titled “Demonstration of Non-Corrosive, Capacitance-Based Water-Treatment Technology for Chilled Water Cooling Systems” evaluated sites at four military installations in Arizona, California, and Georgia. The study included systems where the technology was previously installed as part of a 2010 evaluation (ERDC/CERL TR-09-20) and added systems that broadened the range of water qualities and operating conditions evaluated.
Results and observations indicated that the technology delivered an average 20% reduction in makeup water usage and 50% reduction in blow-down, while meeting or exceeding criteria for protection of equipment from scale, corrosion, and biofouling. Reductions in make-up water represent a major water savings for an installation, while reductions of blow-down water represent a significant lessening of load on installation’s wastewater treatment system. (The direct use of the blow-down water for grey-water purposes appears feasible, but was not demonstrated.)
The technology was effective in water treatment and deposit control for a wide range of water conditions, from very soft, corrosion-promoting water to very hard, scale-promoting water. The validated applications are recommended for consideration by decision makers to reduce military installation chemical utilization and support Department of Defense Net Zero Water goals.
Click Here to link to the Full Study: “Demonstration of Non-Corrosive, Capacitance-Based Water-Treatment Technology for Chilled Water Cooling Systems” Report Number: ERDC/CERL TR14-15
Cooling Tower Institute (CTI) Green Technologies 2012
“Demonstration of Electronic Capacitor-Based Water Treatment System for Application at Military Installations” Report Number: ERDC/CERL TR 09-20
Demonstration of Noncorrosive, Capacitance-Based Water-Treatment Technology for Chilled-Water Cooling Systems : ERDC/CERL TR-14-15
20% reductions in cooling tower make-up water and 50% reduction in blow-down were achieved at four U.S. Military Bases over a 24 month study period.
Zeta Library Collections: FAQ's
What is a Zeta Rod® System for Home Water Conditioning, and is it affordable? The Zeta Rod® green technology offers a highly economical and environmentally sound method of water conditioning that uses the physical and electrochemical effects of electrostatic fields to disperse bacteria and nano-crystals that form biofilm and scale. A Zeta Rod system will normally pay for itself in chemical savings (salts), water conservation (no back-flushing) and maintenance over a period of months rather than years.
Are you interested in protecting and reducing maintenance on evaporative cooling equipment, significantly extending the life of cooler pads and CELdek® media, conserving water, and eliminating odor and scale buildup? Zeta Rod® electronic capacitor-based water treatment systems deliver these benefits and more with a simple installation into the main water line feeding one or more evaporative coolers. Continue reading
The U.S. Army Corps of Engineers Construction Engineering Research Lab has published findings of a two-year Demonstration Validation Study that successfully compared Zeta Rod® Water Management Systems in side-by-side cooling tower installations against standard chemical water treatment programs.
The study, entitled “Demonstration of Electronic Capacitor-Based Water Treatment System for Application at Military Installations” presents the data and results of the study.
Abstract: The United States Department of Defense (DoD) has a specific legislative mandate to increase its conservation of water and energy. It also is interested in improving the effectiveness of open-loop, cooling water treatment processes at its installations worldwide, for purposes of extending the useful life of evaporative cooling equipment and reducing energy use/costs. A Cooperative Research and Development Agreement (CRADA) was approved to demonstrate that, without using chemical additives, a capacitor-based water treatment system is capable of (1) providing equivalent protection to a chemical treatment program in preventing scale, corrosion, and bio-fouling; (2) allowing cooling systems to be operated in an enhanced water conservation mode; (3) delivering measurable reductions in water usage over conventional methods; and (4) providing control, monitoring, and wireless data transfer via the Internet. Results documented in the subsequent demonstration and evaluation project showed the technology was able to meet every objective and also was able to deliver a 20% reduction in cooling water use over standard chemical treatment methods. Application of this technology would allow the DoD to (1) reduce chemical usage, exposure, and disposal expenses; (2) conserve water and energy; (3) facilitate water re-use; and (4) meet new goals for conservation of resources.
To read more, click here to link to the Army Corps of Engineers published study
Zeta Library Collections: Technical Papers
R. Romo, M. M Pitts and N. B. Handagama. "Biofouling Control in Heat Exchangers Using High Voltage Capacitance Based Technology" ECI Symposium Series, Volume RP5: Proceedings of 7th International Conference on Heat Exchanger Fouling and Cleaning - Engineering Conferences International, Tomar, Portugal, July 1 - 6, 2007
…Four different application case studies are presented in this paper in which High Voltage Capacitance Based (HVCB) technology was used to control biofouling. The applications include an evaporative cooling wall in a greenhouse in Oracle, Arizona; a cooling tower–condenser application in Phoenix, Arizona (study performed by Arizona State University under a U.S. Department of Energy grant); a cooling tower system using reclaimed industrial waste water at a wafer facility in Camas, WA; and a piping system for a major utility plant (Tennessee Valley Authority – TVA) using river water.
Tucson, Arizona: Zeta Corporation has established that its patented Zeta Rod® technology is another weapon in the battle against legionella. Zeta Rod systems will remove and prevent recurrence of biofilm and associated scale that shelters legionella bacteria inside potable water systems and in cooling towers. Continue reading
Zeta Library Collections: Case Studies
Biosphere 2: Prevention of Biofouling and Scale in CELdek Wet Wall
Bioshere 2 experiences dramatic improvement in the cleanliness of wet wall CELdek® media with use of Zeta Rod systems. Expected media replacement was unneccessary and the climate wall can operate at peak efficiency.
Click here to link to the Biosphere 2 Wet Wall Case Study